What Is A Backflow Device And Why Do I Need It Tested?
- Categories: Ravinia Plumbing
- Date: February 14, 2012
A backflow device is also known as an RPZ valve. RPZ stands for Reduced Pressure Zone. This device is installed onto your plumbing system to protect your drinking water and the city water supply from contaminants.
RPZ valves are required when a house or building is equipped with an irrigation system, fire suppression system, or a large boiler (hereinafter referred to as Systems). Contaminants can enter an irrigation system from fertilizer or pesticides that are sprayed onto lawns. In the case of a boiler or fire suppression system, water sits stagnant or trapped in these systems, which leads to a build-up of bacteria and increased mineral content from the piping system.
If there is a water leak in the house, house water service break, city water main break, hydrant flushing, or hydrant use due to a fire, the water pressure in the house or city water mains can drop lower than the water pressure in the Systems. This can cause water from the Systems to back-up into the drinking water supply. The next time you or a neighbor turns on a faucet for a drink of water, the water received could contain contaminants. Even small fluctuations in city water mains that occur due to uneven water use from one neighborhood to the next can cause drops in pressure large enough to cause a back-flow and therefore contamination to occur.
If a drop in city or building water pressure occurs, the RPZ valve will open up, dumping water out rather than allowing the potentially contaminated water to back-flow into the water supply. For these reasons, Illinois State Law requires the use of an RPZ as outlined in the Illinois State Plumbing code and Illinois Environmental Protection Agency. All city governments must comply with these laws. The law not only requires the use of an RPZ device but that device must be tested once every year. Only a licensed plumber with a Cross Connection Certification License can test and certify the proper operation of an RPZ valve. Once the RPZ is tested, the certification paperwork is forwarded by the plumber to the city.
It should also be noted that no building, house or system that currently requires protection by an RPZ is “grandfathered” from not having the proper device installed.
For your convenience, Ravinia Plumbing & Heating Co. can provide you with an annual reminder to have your RPZ certified to stay in compliance with your city. Please call us at (847) 432-5561, e-mail us at info@RaviniaPlumbing.com or visit us online at www.RaviniaPlumbing.com for these free maintenance reminders.
Family Owned Since 1928
1580 Old Skokie Rd
Highland Park, IL 60035
P: (847) 579-5565
F: (847) 831-5694
Hours of operation: Mon.-Fri. 8:00-5:00, Sat. 8:00-1:30
View Location on a Map
5 Reasons to Schedule Maintenance for Your Home’s Air Conditioner Now
April 26, 2018
Maintenance is an important part of homeownership, and while it does come at a cost, it can pay for itself in most cases. This is especially true Read more…